Victron Multiplus 24/2000/50 2000W Pure Sinewave Inverter Charger
The Victron Multiplus C 24/2000/50 2000W Pure Sinewave Inverter Charger is, in one compact housing, a powerful sine wave inverter, a sophisticated charger
adaptive technology batteries and AC transfer switch at high speed. In addition to these
main functions, the MultiPlus has several advanced features, as described below.
Two AC outlets
The main output has the “no-break.” The MultiPlus is responsible for the supply burden
connected during a power failure or disconnection of the mains-generator. This happens so fast (less than
20 milliseconds) that computers and other electronic equipment continue to operate without
The second output is only active when one of the inputs of AC arrives MultiPlus. This
output can be connected appliances should not discharge the battery, like a water heater by
example (second exit available only on models with 50 amp transfer switch).
Virtually unlimited power thanks to parallel operation
Up to 6 Multi’s can operate in parallel to achieve higher power output. Six units
24/5000/120, for example, will a power output of 25 kW/30 kVA and a load capacity of 720
Three phase capability
In addition to parallel connection, three units can be configured the same model for an output
phase. But that’s not all may be connected in parallel up to 6 sets of three units
provide an output power of 75 kW / 90 kVA and over 2000 amps of capacity.
PowerControl – limited generator, shore-side or network
The Multi is a very powerful battery charger. Therefore, use lots of electricity from the generator or the network
the dock (about 10 A per Multi at 230 VAC 5kVA). The Multi Control Panel can be established
maximum generator power or shore. The MultiPlus will take account of other AC loads
and use the excess power to the load, thus avoiding overloading the generator or shore supply from.
PowerAssist – Increase the power capacity of shore or generator
This function takes the principle of PowerControl to another dimension. Allows the MultiPlus to supplement the
alternative source capacity. When required, a peak power for a short space of time,
as often happens, MultiPlus immediately compensated the possible lack of power of the current
shore or generator with battery power. When the load reduces, the spare power is used
to recharge the battery.
Variable four-stage charger and battery banks charging double
The main output provides a powerful charge to the battery system using an advanced software
“Variable load.” Software fine-tunes the three stage automatic process to adapt to the
battery conditions and adds a fourth stage for long periods of slow loading. The process
variable load is described in more detail in the Phoenix data sheet Charger and our web site, the
see “Technical Information.” Besides this, the MultiPlus can charge a second battery
using a limited carrying out independent, designed to charge a battery to start the engine
main or the generator (this exit only available in 12V and 24V models).
The system configuration can not be easier
Once installed, the MultiPlus is ready for operation.
If the configuration has changed, you can make in minutes using a new procedure
DIP switch configuration. With the DIP switches can even schedule
parallel operation and the phase: no computer needed!
You can also use a VE.Net instead of DIP switches.
And there are sophisticated software (Quick Setup and VE.Bus VE.Bus System Configurator) to set
several new and advanced features.
Victron Multiplus 24/2000/50 2000W Pure Sinewave Inverter Charger features
|Input Battery Voltage Range
|19 – 33 V
|Nominal AC output Voltage
|230 VAC ± 2%
|Continuous Power Rating
|2000VA at 25 °C
|Peak Inverter Efficiency
|Pure Sine Wave
|Nominal DC Input Voltage
|AC input Voltage Range
|Frequency Range AC Input
|45 – 55 Hz